Aluminum Fire Alarm Station With Pull-ring Activation
Enclosure Is Made Of Copper Free Aluminum Alloy. Conduit Openings Are 3/4" Npt Feed Through. Red, Textured Powder Epoxy Paint Finish Is Standard On Box And Cover And Provides High Visibility For Alarm Station. Has (1) Normally Open And (1) Normally Closed Contacts. Bilingual Nameplates Included Per Csa Requirement. Internal Ground Screw Is Standard. The Alarm Station Is Activated By Lifting The Front Cover And Pulling Down Ring. This Quick, Easy To Use Two-step Process Prevents Unintentional Operation. Operator Is Reset By Depressing Shaft And Returning Plate To Original Position.
Hazardous Areas Due To The Presence Of Flammable Gases Or Vapors, Combustible Dusts, Or Easily Ignitable Fibers Or Flyings. Installation At Petroleum Refineries, Chemical And Petrochemical Plants, Storage Areas, And Other Processing Facilities Where Hazardous Substances Are Handled Or Stored. Areas Where Emergency Control Of Fire Alarm Or Signal Circuits Is Required.
Number Of Poles
7200 Va (make), 720 Va (break), 10a Cont. @ 600v Ac; 2.5a Cont. @ 600v Dc.
6-27/64" H X 3-7/64" W X 4-9/64"
Xal/xas Series Controls Fire Alarm Stations
This item is listed as MANUFACTURER NON-STOCK.
Quantity Discount Pricing
Order a combined total from KILLARK ELECTRICAL PRODUCTS in the ranges below to receive a discount applied to all of their products.